The instrumentation and automation package is equipped with a power supply, ventilation, heating, fire alarm systems. The package is designed for 4 instrumentation and automation control cabinets and a distribution cabinet РЩ-230В.
Scope of Delivery:
- building with instrumentation and automation completed with equipment and internal engineering networks;
- building passport;
- data sheet for component parts;
- spare parts set;
- technical and design documentation in Russian (3 copies) and their PDF soft copies on a CD.
The ББТ-АММА instrumentation and automation package can be transported by road, rail or sea (river) in accordance with the current rules of transportation for the particular type of transport.
Regarding the climatic factors, the unit can be transported as per group 8 of GOST 15150-69. Regarding physical impact factors, the transportation standard is GOST 23170-78.
Before transporting dismantle and secure all the removable parts of the ББТ-АММА instrumentation and automation package as per instructions of this Operation Manual.
Only serviceable packages with intact lifting lugs are allowed for transportation.
The ББТ-АММА instrumentation and automation package shall be loaded onto the vehicle by means of cranes of suitable lifting capacity, equipped with lifting and pulling devices.
The ББТ-АММА instrumentation and automation package is allowed to be lifted only using the elements designed for lifting.
Otherwise lifting of the ББТ-АММА instrumentation and automation package is prohibited.
The ББТ-АММА instrumentation and automation package shall be secured in the vehicles in accordance with the handling and securing specifications for each type of transport.
The overall dimensions of the ББТ-АММА instrumentation and automation package shall comply with the requirements of the handling dimensions from the Techncial Specifications for Handling and Securing Cargoes by the Ministry of Transport of Russia.
The heating devices are electrical heaters.
Temperature controllers are mounted on the heaters to adjust the temperature mode. The heaters should be placed under light openings and by the external walls.
In the instrumentation and automation package modular container there is a natural inflow of the fresh air through loose elements.
Inside there is an exhaust naturally-forced ventilation through regulated ventilation grilles.
To create and maintain best air conditions in summer the instrumentation and automation package modular container has a split system.
The instrumentation and automation package is powered according to the international requirements of EIC.
The power circuit has 400/230 V voltage and dead-earthed neutral earthing (TN-C-S). The set capacity of the connected load is 4.68 kWt, the design capacity is 3.93 kWt. The distribution circuit is made with a cable ВВГнг-LS laid in cable trays.
The internal earthing is made with a steel strip 25x4 laid 0.4 m above the floor. The lightning protection is ensured with metal parts of the package to the earthing device with two conductors.The resistance of the earthing device in any season of the year will not exceed 4 Ohm.
For protection against direct lightning strikes and its secondary manifestations, the metal structure of the building is connected in two places by a 40×4 steel strip to the grounding loop.
AMMA guarantees that the ББТ-АММА instrumentation and automation package complies with the technical documentation, provided the customer maintains the conditions of transport, storage, mounting and operation.
The warranty period is 12 (twelve) months from the date of mounting or 18 months from the date of delivery, whichever comes first. The service life of the ББТ-АММА instrumentation and automation package is 8 years.
The warranty periods for the components used in the ББТ-АММА instrumentation and automation package are specified by the manufacturer, who is responsible for their quality.
A warranty period may be agreed upon with the Customer.